Q. How long can my generator run before I need to check the oil?
A. We recommend checking the oil level after every 8-24 hours of operation, depending on the size and model of the generator. Oil change and filter change frequency and other routine maintenance varies per model, especially during periods of extended power outage. Check the Operation Manual included with your generator for a complete list of required maintenance procedures and schedules.
Q. How do I check the engine oil?
A. (1) Power off the generator and let the engine sit for two minutes to settle the oil. Pull the dipstick from the back of the engine and wipe with a clean rag. Insert the dipstick back into the dipstick tube and pull it out. Note the crosshatching on the end of the dipstick, from “F” (Full) to “L” (Low), and see where the oil level falls. Add oil if the dipstick indicates that the oil level is low.
(2) Locate the yellow oil-access cap on the front of the engine (look for the oil can icon). Add a few ounces of oil, then recheck the oil level by inserting and removing the dipstick. Add oil until the level is near “F.” Do not overfill the engine.
(3) When you’re finished adding oil, make sure the dipstick and oil access cap are securely in place. Push the AUTO button to place the generator back in standby mode. If the utility power is still out, the generator will start within three seconds. After the generator starts, move the circuit breaker to the ON position so the generator is now supplying power to the house.
Q. Where is the oil dipstick?
A. The dipstick has a bright yellow ring attached to the end. The location varies by generator, but it's typically noticeable as soon as you open the access panel or hood.
Q. What type of oil should I use in my generator?
A. Your generator ships with Mobile 1 5W30 full-synthetic oil, which is the oil Kohler recommendeds. Although a synthetic blend may be used, our recommendation is full-synthetic oil. However, if you know that the oil has been changed out to conventional oil, then use only conventional oil from that point on. Do not mix synthetic oil with conventional oil.
Q. How much oil does a generator normally use?
A. The amount varies and depends on engine model, length of time since the last oil change, amount of power the generator is produceing and length of the power outage. Check the Operation Manual included with your generator for a complete list of required maintenance procedures and schedules.
Q. What should I do if the generator is submerged in water?
A. Water and electricity are a very dangerous mix. If you can safely access it, power off the generator. (See How do I manually "power off" the generator set?) If it continues to run when submerged, internal damage to both engine and generator will be significant. If you can't safely access the generator or the main-line disconnect, do not make any attempt to turn it off.
Q. How do I register my generator's warranty protection?
A. To register your warranty, have a South Shore Generaror technician complete a post-installation Warranty Start-Up at your home. Then, instead of your warranty beginning on the day the generator is purchased, it begins on the day your service technician submits your generator system's details to the Warranty Start-Up program. The technician completes a checklist, makes sure the system is properly installed, and enters all necessary information onto the Kohler Warranty site. This moves the warranty start date to the day your generator is installed, instead of the date it left the factory.
For more information contact South Shore Generaror.